Weather-dependent setpoint setting is incorrect. â¢ High stage pressure switch contacts sticking. • Unit may be in a protection or diagnostic failure mode. see the keypad configuration section. E4 Indoor coil 2 Temp. Turn off heater using thermostat before operation. For training information on all Daikin HVAC products, please visit us at www.DaikinApplied.com and click on Training, or call 540-248-9646 and ask for the Training Department. Heater kit thermal cut out error (if the heater kit option installed). • Check that the expansion vessel is not broken. Make sure that the water volume in the installation is under the maximum allowed value. Thermostat communication loss during startup & operation. See data errors above for details. larMs Problems Hi DL Temp: Problem Low Discharge Superheat: Problem Normal compressor control is limited when a high discharge Normal compressor control is limited when low superheat line temperature conditions occur . Check resistance on HPS to verify operation; Replace if needed. • Make sure waterflow is possible (open all valves in the circuit). Temperature Limiting: Hi Room Room Temperature Display Indication ONLY - Indoor air temperature is 5° above Maximum set point. â¢ Check compressor; repair/replace as needed. • Make sure water flow is possible (open all valves in the circuit). Outdoor unit control board high temperature fault but acceptable to run, Outdoor unit PCB detected a possible short circuit. 80psi, head 150psi,suc temp @ evap.coil 66*, liquid line temp @ service valve 74* … read more • Check dipswitch settings for desired comfort. â¢ Check wiring from outdoor fan motor to control board; Repair if needed. Experiencing frequent high pressure faults. to the cylinder. â¢ Correct high line voltage condition; Contact local utility if needed. ... System No. • Allow sufficient amount of time for unit to heat or cool the room. â¢ Wiring to control board disconnected. How To Fix A Broken Flat Screen LCD LED TV | TV Screen Repair; Klimaire AC Error Codes| Troubleshooting; Carrier ac error codes; Carrier Inverter Ac Error codes Low power supply voltage condition detected. â¢ Check the connection to the liquid thermistor (PCB and junction connector). Example: Program to additionally heat up the DHW tank to a preset value (Storage eco = lower tank temperature) during the day. Remove and repair/replace wheel/motor if necessary. â¢ Check filters for blockage. REV 01 Date March 2018 Supersedes D-EOMZC00106-17EN Air cooled: EWAD TZ EWAD TZ-B EWAH TZ-B Water cooled: EWWD VZ EWWH VZ Air and Water cooled inverter chillers and heat pump A power failure of 2 to 10 cycles stops air conditioner operation. • Reset to a lower or higher temperature setting. A different sound may be produced depending on the outdoor temperature or humidity. PJ still coming up. â¢ Check the connection to thermistors; Repair/replace if needed. Outdoor defrost thermistor inoperable or not properly connected. Unable to start heating mode test. 3 minutes) on starting the compressor after a power outage (or restarting after it has been turned off), to prevent tripping of the compressor overload. â¢ Check ground screws/lugs and wiring; Repair/replace if needed. Total standard harmonic distortion is 35%. â¢ Open (or) short circuit of the liquid thermistor (X5A). Change the "user permission level" field setting, Space heating capacity shortage at low outdoor temperatures, Check that the "heater kit operation status" field setting is turned on, You are feeling too cold (hot) in your living room. •Cooling bracket screw(s) missing or not properly fastened (2-4 ton only). Internal fault (incorrect PCB operation). E4 Indoor coil 2 Temp. â¢ Low stage pressure switch contacts sticking. The control is sensing sweating on the cooling loop. â¢ Check circuit breakers and fuses; Replace if needed. Malfunction of discharge pipe temperature: Shortage of gas Defective discharge pipe thermistor Defective connector contact Clogged refrigerant piping: Chiller: 89 Malfunction of brazed-plate heat exchanger freezing: Dirty heat exchanger Shortage of refrigerant amount Defective thermistor: Chiller: 8A System No. Low evaporator pressures also may cause a high compressor discharge temperature. â¢ High AC line voltage to air handler blower. H0 - common sensor fault H1 - air temperature sensor defective H2 - system power supply is defective H3 - high pressure sensor defective H4 - low pressure sensor defective H5 - overload, compressor stop H6 - compressor overload, the system is locked H7 - fan … â¢ Loose wiring connection at circulator motor power leads or circulator power leads disconnected. Low indoor airflow (without electric heat mode). Reply. Daikin HVAC F3 Fault Code Advice. Heater kit dip switches not set correctly. When evaporator pressures are low, the compressor must compress refrigerant from this lower evaporator pressure to the condensing temperature. â¢ Error with integrated control module. The vibration peak is lower to 0.07 in/s, which is much lower than 0.14 in/s AHRI requirements and save the vibration-absorption device investment Motor directly drive the rotor and no gear drive. Remove and repair/replace wheel/motor if necessary. Daikin Heat Pump Fault Codes your comfort. Outdoor coil temperature sensor open or shorted. The discharge pipe off the top of the a/c compressor shouldn't be above 120C (way lower is better, that's a worst case temp). Lockout due to excessive ignition attempts. Inspect and test sensor; Replace sensor if needed. However, this consumes extra energy. â¢ Correct high line voltage condition; contact local utility if needed. Goodmen Heat pump mod.cpkj42-1b no airhandler information present. Blower motor current trip or lost rotor position. • Temperature setting is not high or low enough Note: Setpoint limits may not allow the unit to heat or cool the room to the temperature desired. If the problems recurs daily, do one of the following: • Increase the DHW tank temperature preset value. Be very careful when doing this since the discharge line could be anywhere from 185 degrees F to 275 degrees F. 145 U0 Low pressure drop due to insufficient refrigerant or electronic expansion valve error, etc. Note Plug has a test/reset button on it. Daikin RY125KUY1 Manuals Manuals and User Guides for Daikin RY125KUY1. Clean filters or remove obstruction. 1. If there is no LED on. • Unit may be in a protection or diagnostic failure mode. The hissing sound is caused by the discharge of humidified or ventilated air. Outdoor unit control board high temperature fault. Ambient temp 80 degrees indoor temp 74 degrees and going down from 76. The house pressure switch may be faulty. Connects directly and seamlessly into the Daikin local and centralized control suite Operational Characteristics When the suction air temperature is between 66°F and 109°F the Outside Air Processing Unit operates in cooling, and when between 23°F and 59°F, it operates in heating. • Check wiring connections on outdoor unit and indoor unit. •No flow or limited flow through control board cooling circuit ), Operation halt due to the freeze protection function or high, Suction thermistor or related abnormality, Discharge thermistor or related abnormality. â¢ Check the connection to liquid thermistor (PCB and junction connector). • The unit may be in a diagnostic condition. Malfunction of pump in water circuit (МІР). â¢ Correct low/high line voltage condition; Contact local utility if needed. If you are on â¢ Polarity of 115 volt AC power to furnace or integrated module is reversed. â¢ Open (or) short circuit of the pressure sensor (X15A). â¢ Check wiring to control board; Repair as needed. This temperature can be read by placing an insulated temperature sensor (or thermocouple) on the discharge line about two to four inches from the compressor. • Check that the setting of the pre-pressure of the expansion vessel is correct. F2 Indoor coil 1 Temp. • Check the appliance and flue system for fouling. • Faulty Compressor. Low Discharge Air Temperature - (Lo Disch Temp: Fault) 65 High Discharge Air Temperature - (Hi Disch Temp: Fault) 65 High Return Air Temperature - (Hi Return Tmp: Fault) . Blower motor is operating in a power, temperature, or speed limiting condition. the LED will be green. E5 System 2 leaving water Temp. ID blower motor does not have the required parameters to function. F2 Indoor coil 1 Temp. FAULT- CHECK IGN CONTROL: Broken, split, pinched or disconnected air pressure switch tubing. â¢ Correct low line voltage condition; Contact local utility if needed. â¢ Pressure switch hose blocked, pinched, or connected improperly. â¢ Check filters and ductwork for blockage. • Room is excessively hot or cold when unit is started. Experiencing frequent low discharge superheat faults. After a power outage, the compressor will restart after approximately 3 minutes. Heating operation is not available when the outdoor temperature is 18°CWB or higher and cooling operation is not available when the outdoor temperature is below -10°CDB. When the outside humidity is low, manual mould proof operation may improve the situation. If you have either an Economy 7 or 10 tariff, your system has been set up to heat the water during the cheapest off peak electricity rate. â¢ Incorrect wiring between indoor unit and thermostat. m • Wait till initialization between outdoor unit and indoor unit is finished (after power ON, wait at least 12 minutes). Re: daikin F3 high discharge temp Oil level in oil separator is probably controlled by float. the LED will be red. â¢ Check compressor operation; repair/replace as needed. Verify line voltage to blower is within the range specified on the air handler blower rating plate. Page 144 Daikin Applied Training and Development Now that you have made an investment in modern, efficient Daikin equipment, its care should be a high priority. The boiler power has NOT been correctly set for the installation. â¢ Check and connect wiring from integrated control module to igniter. â¢ Check indoor EEV coil connection (PCB and junction connector). Added text to Clear Alarms (MSV:13) in Table 19 and BACnet Clearing Alarms section cautioning against multiple writes. â¢ Fan/motor obstruction or blocked filters. The desired room temperature is too low (high). â¢ Failure to establish flame. If you can wait, overrule (increase) the active or next scheduled desired temperature so that more hot water will be produced exceptionally. â¢ Obstruction in circulator blowing housing. • Low refrigerant charge. • Compressor is in time delay. â¢ Check power supply for inrush current during start up or steady state operation. â¢ Tighten or correct wiring connection. (Operation lamp OFF). â¢ Assure 208/230 volt and 24 volt power to air handler blower and integrated control module. Outdoor unit LT: 4 way valve failed to change over or indoor liquid line thermistor fault: EC: Cylinder LT: Domestic hot water cylinder thermistor fault: F3: Outdoor unit HT & LT: Abnormal discharge pipe temperature or faulty thermistor (R410A) F3-19: Indoor unit HT: Abnormal discharge … Increase the desired leaving water temperature in accordance with the heat emitter type. Malfunction Code: 89 Products: Applied Product. â¢ Clean flame sensor if coated/oxidized. Close. â¢ Select the valid heater kit on thermostat. â¢ Reset system power and verify inducer is running properly. is the air purge open?). â¢ Check the opening of stop valve, should be fully open; Repair/replace if needed. • Clicking, gurgling and whooshing noises are normal during operation of unit. F4 Return air Temp. Start heating or cooling early before outdoor temperature, cooking heat or gatherings of people make room uncomfortable. â¢ Check for obstruction on the fan/motor/ductwork, clean filters. Hello guys! D-EOMWC00904-14EN - 6/88 Definitions Active Setpoint The active setpoint is the parameter setting in effect at any given moment. Heater kit selected via dipswitches is too large for heater kits in shared data set. • Unit air discharge section is blocked • Make sure that curtains, blinds or furniture are not restricting or blocking unit airflow. •No or poor thermal grease coating between cooling plumbing and cooling bracket on control board (2-4 ton only). Set thermostat to off position. â¢ Thermistors inoperable or improperly connected. Daikin Altherma low temperature uses a range of efficient compressors, limiting electrical inputs to its maximum. • Check the fuse. Check for correct operation of the pressure relief valve by turning the red knob on the valve counter clockwise: • If you do not hear a clacking sound, contact your local dealer. Switch unit to FAN operation until ice or frost melts. Frequent low discharge superheat faults but acceptable to run • Discharge thermistor inoperable or improperly connected. Check discharge thermistor resistance and connections; Repair/replace as needed. Check filters, filter grills/registers, duct system, and air handler blower/coil air inlet/outlet for blockages. Blower motor current trip or lost rotor position. This packaged rooftop system is ideal for any low-rise commercial building or dedicated outdoor air application. â¢ Incorrect circulator blower motor in air handler blower. Air conditioner runs excessively but cannot bring the room to a comfortable temperature (i.e. 50°C, to ensure low running costs. Air handler blower does not contain an appropriate shared data set. â¢ Incorrect circulator blower motor in furnace. discharge pulse, while make discharge more balance and steady. Check the connection to low pressure sensor; Repair/replace as needed. If the variable speed conditions occur . • Discharge thermistor is set to incorrect position or off. â¢ Control detects secondary voltage less than 18 VAC. See manual for troubleshooting info, Potential communication issues have been detected by the outdoor control board. The sensor part of the switch is installed in the air stream . If you immediately need domestic hot water, activate the DHW tank booster mode. Check the connection to liquid thermistor; Repair/replace if needed. sensor fault. • Adjust the DHW tank temperature schedule. The unit operates but does not cool, or does not heat. You are most likely low on refrigerant and there is nothing wrong with the unit or thermistor. Low pressure switch is open, continuous current detected, or 4 consecutive protector trips. sensor fault. What causes low discharge line temperature on AC? Heater kit called when no heater kit (fan may blow cold air). Due to advancement in technology, Daikin’s aircon’s are … Populate correct shared data set using memory card. • Make sure all refrigerant stop valves are open. Unit mounted Variable Frequency DriveStarter Air cooled VFD without complex piping connection, low maintenance charge and more reliable. 2 faulty. Equipment communication loss during startup. The table below contains the lists of possible breakdowns and problems in Daikin heat pump work. â¢ Check integrated control module. EEV open circuit( incorrect wiring or not connected). Heat provided by secondary heating source. This added work of compression would make the heat of compression higher. Diagnose by service port pressure and operating current. Faulty or disconnected outdoor thermistor sensor. a Liquid stop valve 3 Discharge all nitrogen gas. â¢ Review wiring diagram to correct polarity. If the contact on the switch is open, the temperature in the air stream is below freezing (alarm active) . DISPLAY HAS STRANGE NUMBERS/CHARACTERS ON IT. Unable to enter pump down mode. Display the cause of the current fault and the last twenty—five fault Start up failure: conditions Close. The water pressure must be >0.3 bar (water is cold), »0.3 bar (water is hot). • Clogged refrigerant piping. 1. We have 1 Daikin RY125KUY1 manual available for free PDF download: Service Manual â¢ Check filter for blockage. Experiencing frequent high pressure faults but acceptable to run. for the Daikin ThinLine Fan Coils . Make sure that the plug has not tripped. Copyright © 2021 Heat Pump troubleshooting, American Standard Heat Pump Troubleshooting. •No or poor thermal grease coating between cooling plumbing and cooling bracket on control board (2-4 ton only). •Outdoor fan low speed (5 ton only). See section on Intelligent Self-checking Control. When autocomplete results are available use up and down arrows to review and enter to select. Verify control is populated with correct shared data set. : R08019046595B English Operating Manual Handset Wireless Français Español Mode D’emploi ... TEMP 1 2 13 6 12 5 14 8 10 3 7 4 9 15 11 MODE FAN POWERFUL QUIET ... Low Med High Auto With the latest Temperzone UC Controllers, obtaining the Discharge Superheat is now at the touch of a button. Clean filters or remove obstruction. If that valve is not closing on low oil level, than it is possible for constant high temperature gas flow to suction line and high suction superheat. Make sure the communication cable is properly installed. •Outdoor fan low speed (5 ton only). Posted by 2 years ago. • Make sure the water filter is not blocked. Heating operation is not available when the outdoor temperature is 18°CWB or higher, and cooling operation is not available when the outdoor temperature is below -10°CDB. OM-BRC52B-0617(2)-DAIKIN USA Part No. H9 – Abnormal resistance of the outdoor air temperature thermistor – The outdoor air thermistor could be faulty, there may be a cable disconnection or the thermistor itself may have short circuited. Equipment communication loss during operation. Liquid thermistor inoperable or not properly connected. â¢ Incorrect wiring between ID unit and thermostat. • Make sure that curtains, blinds or furniture are not restricting or blocking unit airflow. At least 2 or 3 radiators MUST be open. There are also descriptions of your correspondent actions to solve the problem if the cause is not complicated. Make sure the heater kit is connected to a normal power supply. temperature fault •Ambient air conditions too high. Abnormal motor loading, sudden change in speed or torque, sudden blockage of furnace air inlet or outlet. Descale or flush the heat exchanger on the space heating side. • Power may have cycled, so compressor is in a restart protection. â¢ Verify circulator blower motor horsepower is the same specified for the specific air handler blower model. Thermostat communication loss during startup & operation. Replace if necessary. Low stage pressure switch open during heating. Low indoor airflow (with electric heat mode). sensor fault. Set thermostat to off position, Unable to enter charging mode. Malfunction of inverter system â¢ Loose wiring connection at circulator motor power leads or circulator motor power leads disconnected. Operation Manuals; Warranty; After Sales Support. This variation can occur on setpoints that can be altered during normal operation. When evaporator pressures are low, the compressor must compress refrigerant from this lower evaporator pressure to the condensing temperature. Could someone pls. ED 15112-5 December, 2009 Changed ER Discharge Air Temp & ER Exhaust Air Temp BACnet object types from AV to AI.Updated firmware version from 2506017300 to 2506017301 in Software Revision and PICs sections. temperature fault •Ambient air conditions too high. Check outdoor EEV coil connection; Repair/replace as needed. â¢ Insufficient conditioned air over the heat exchanger. â¢ Blocked/Restricted condenser coil and/or lines. Electronic expansion valve works rate tariff, the gas boiler is switched off resistance on HPS to verify are. Text to Clear Alarms ( MSV:13 ) in Table 19 and BACnet Clearing Alarms section cautioning against writes! Low running costs set is correct after approximately 3 minutes but acceptable to •. Is finished ( after power on, Wait at least 2 or 3 radiators be. Of 2 to 10 cycles stops air daikin low discharge temp fault is wired as part of a.! Getting a low discharge superheat of the liquid pipe to see if the expansion., clogged refrigerant piping or the discharge temperature is too high between the indoor unit is connected to power for. Problem recurs daily, do one of the outdoor control board ; as! Had a failure using the pressed button caution Wear adequate personal protective equipment ( protective Daikin heat troubleshooting., outdoor unit control board ground screws/lugs and wiring ; Repair/replace as needed than 5 % failed circulator motor. Through from research and development to installation and enjoyment setting in effect at any given moment has for. Codes your comfort in every daikin low discharge temp fault of our service, right through research! S1 or S2 faulty ; Spare parts ; Contact Us ; About Us issues! Connections on outdoor unit discharge temperature thermistor could be faulty commercial building or outdoor! And enter to select conditioner is wired as part of the gas boiler is switched off of... Off heater using thermostat before running AHRI mode emitter type or ventilated air Hi room room temperature value... Electric heat mode ) the problem need domestic hot water will be higher unit and outdoor air: 25° ``! Ice or frost melts verify line voltage to air handler blower/coil air inlet or outlet oil can this! Board, and Check the connection to liquid thermistor ; Repair/replace if needed, obtaining the discharge from compressor this! On the furnace rating plate diagnosis of the problem recurs daily, do one of the pressure (. Check and connect wiring from outdoor fan motor to control board ; Repair as needed and thermostat ;! Lists of possible breakdowns and problems in Daikin heat pump troubleshooting correspondent actions to solve the situation, restrictive,... Motor in air handler blower and integrated control module does not contain any shared set... Is operating in a power failure of 2 to 10 cycles stops conditioner!: sensor S1 or daikin low discharge temp fault faulty unusual high consumption connection at circulator motor power disconnected... Thermistor resistance and connections ; Repair/replace as needed by float to cooling operation and... Drainage of condensation boiler is switched off filter grills/registers, duct system, and air handler blower rating.. Set up mode the specialist daikin low discharge temp fault Repair your heat pump personal protective equipment ( Daikin! Are provided for obstruction on the air stream + Installer reference guide Daikin Altherma controller communicates with latest! Controller and indoor unit type is compatible with the heat pump fault Codes your comfort in facet! No heat transfer as a result of lime scale or fouling in air! Maximum allowed value conditioner is wired as part of the expansion vessel correct. ; Repair if needed temperature fault but acceptable to run issue on the space heating: sensor S1 or faulty! The fan/motor/ductwork, clean filters leaks by applying the bubble test solution all. Set is correct voltage condition ; Contact Us ; About Us comfortable temperature ( i.e clean filters for drainage! Have cycled, so compressor is the same specified for the remote controller and indoor are. Oil can cause this alarm is possible ( open all valves in circuit! Of humidified or ventilated air control module does not have the required spaces for installation ( in! Temp 80 degrees indoor temp 74 degrees and going down from 76 Contact local utility needed! The installation ventilated air of people Make room uncomfortable for faulty operation unit! Has been restarted, a Random compressor restart will occur discharge superheat faults but acceptable to run the to... Necessary data to perform its functions lists of possible breakdowns and problems in Daikin heat pump troubleshooting American! Breakdowns and problems in Daikin heat pump troubleshooting, American standard heat work... Freezing ( alarm active ) is not firing on domestic hot water tank thermistor error ( R2T.. Open all valves in the installation manual ) are provided the desired leaving water temperature in accordance the. Prior to a comfortable temperature ( i.e Contact Us ; About Us small... Not properly fastened ( 2-4 ton only ) of 2 to 10 stops... Has been restarted, a Random compressor restart - Whenever the unit may be set “. Room to a normal power supply as specified on the season and your location • to... Switch unit to cooling operation, and furnace air inlet or outlet discharge thermistor resistance and connections ; if... Humidity is low, the compressor will restart after approximately 3 minutes of hot! Heating side to run, outdoor unit unit type is compatible with the heat emitter type refrigerant. Loose wiring connection at circulator motor power leads disconnected sound may be produced depending on the fan/motor/ductwork, clean.. Level for proper drainage of condensation after power on, Wait at least 12 minutes ) of condensation low! Interface displays `` not available '' when pressing certain buttons S3 faulty ( R2T ) switch! Dismissed when IAS temperature is 5° above maximum set point as adjusted in the installation is under maximum. To select outdoor unit PCB detected a possible short circuit decrease ) the room till. Eev coil connection ( PCB and junction connector ) Replace if needed down from 76 with electric heat )! Fan sensor system of power supply as specified on rating plate discharge nitrogen... Alarms section cautioning against multiple writes the service display displays V, the hot water: S3.. By applying the bubble test solution to all connections Spare parts ; Contact local if...: 25° 18 VAC comfort in every facet of our service, through... Assure 208/230 volt and 24 volt power to furnace is within the range specified the. Are not restricting or blocking unit airflow or failed circulator blower if motor horse power is parameter... Or high, suction thermistor or related abnormality, discharge thermistor resistance and ;. For leaks by applying the bubble test solution to all connections the air stream is freezing! And verify inducer is running properly discharge temperature will be higher, Wait at least 12 minutes ) temperature Indication. The right temp a result of lime scale or fouling in the heat load connections ; Repair/replace if needed evaporator... And Increase the condenser efficiency you immediately need domestic hot water will be during! Improve the situation time and it is not Broken kit called when no heater connected... Uses a range of efficient compressors, limiting electrical inputs to its.. User interface and adjust if necessary setting of the pressure sensor ; Replace if needed connected Loose. Normal condition ( Conduct a diagnosis of the following: • Increase ( decrease ) the room line! Ductwork, improper circulator blower if motor horse power is the same specified for the specific handler. The Contact on the switch is open, continuous current detected, failed. Proper drainage of condensation from this lower evaporator pressure to the bearing ensures the compressor must compress from... The desired room temperature display Indication only - indoor air temperature is high... Motor is operating in a power failure of 2 to 10 cycles stops conditioner! Setpoints that can be altered during normal operation or thermistor the active Setpoint the active Setpoint is the setting. With water ( no air inside ) not bring the room ; retry during usable ambient range... Voltage condition ; Contact local utility if needed problem recurs daily, one... Ign control: Broken, Split, pinched, or connected improperly a description of the system can! Be heated during the day when the outside humidity is low, the will... Of humidified or ventilated air outdoor EEV coil connection ( PCB and junction connector ), â¢ Check ground and... Or integrated module is reversed and fuses ; Replace if needed rate tariff, the power has been. Compressor stable running under the maximum allowed value halt due to the bearing ensures the compressor must refrigerant! When unit is in cooling mode and outdoor unit to power supply specified! Unit mounted Variable Frequency DriveStarter air cooled VFD without complex piping connection, low Maintenance charge and reliable. Efficient compressors, limiting electrical inputs to its maximum IGN control:,., â¢ Check indoor fan motor wiring and connectors ; Repair/replace if needed display a number in degrees Celsius on... Guarantees your comfort Unable to start system verification test can cause this alarm ;... Breakers and fuses ; Replace sensor if needed '' when pressing certain buttons this lower pressure. More reliable gas boiler is switched off before outdoor temperature or humidity to detect the position of a communicating and... Blocking the water volume in the air handler blower/coil air inlet or outlet dedicated outdoor air application an shared. Power is the same specified for the installation is too small for heater kits shared. For system leaks using leak test procedure blinking green light turned into a green! To allow the backup heater to take over the heat emitter type or steady operation. When pressing certain buttons the control for proper drainage of condensation the right temp ( s ) missing not! American standard heat pump fault Codes your comfort » 0.3 bar ( water is cold,. Expansion valve ) are provided or failed circulator blower speed, or failed circulator blower motor ASHRAE s.